|A1b1||Minimum (K2) and maximum (K1) dP alarms on separate relays||Minimum and maximum dP alarms act on 2 different relays: relay K2 for minimum dP-alarm, relay K1 for maximum dP-alarm.|
|C11a||4÷20 mA output signal of dP readout||4÷20 mA output signal corresponding to the dP reading.
The signal is active, supplied at 12VDC by the device, the maximun drived load is 450 Ohm.
4mA = dP reading 0.00 kPa, 20 mA = dP reading equal to the full range requested.
If an external voltage is applied to C11a clamps the device will be damaged.
• A: Max 450 Ohm
|C13_10||dP full range 10.00 kPa = 100.0 mbar = 1012 mmH2O.||Maximum differential pressure value measurable by the device 10.00 kPa = 100.0 mbar = 1012 mmH2O.
With dP reading over 10 kPa the display shows 'E' instead of the numeric value of dP.
|C3||Differential pressure readout from internal transducer (max 10 kPa)|
|C7c1||Minimum dP alarm. Automatic reset.||If the dP readout is below the threshold set in Set up, the minimum dP alarm is activated.
The display shows the alarm condition code E8 (see the alarm description) or the dP readout and letter L alternatively, according to the model.
The corresponding alarm relay will signal its condition.
The alarm is automatically reset when the dP readout is above the threshold again.
With set value 'OFF' or 'E' (according to the model), the function is excluded.
NOTE: the minimum dP alarm is delayed by 60 seconds by default after the activation of the first cleaning cycle.
|C7d1||Maximum dP alarm. Automatic reset.||If the dP readout is above the threshold in Set up, the maximum dP alarm is activated. The display shows the alarm condition code E7 (see the alarm description) or the dP readout and letter H alternatively, according to the model.
The corresponding alarm relay will signal its condition. The alarm is automatically reset when the dP readout is below the alarm threshold again.
The activation of this alarm is delayed by 20 seconds by default.
|C8||dP zero readout regulation||In this set up code it is possible to adjust the zero reading of differential pressure.
In this function the display shows the dP reading and, with plant stops or air pipes not connected if the dP reading is not 0.00 kPa it is possible to adjust it by key A and C.
|DPa||Air connections 6x4 RILSAN pipe|
|HVC||Input voltage selection||By some jumpers on the board it is possible to change the supply voltage. (See label or board layout).
JP1: Supply voltage selection between 115VAC or 230VAC.