|Options on request. Contact us for other options|
|D11||Emission control by TRIBO-CHECK probe.||By connecting the Tribo-Check probe to the device it is possible to keep under control the dust emission in the duct.
The TC probe management contain some function and possible alarm situations that allow to find if there is a broken bag or a continuos emission over a set threshold.
If there is an alarm situation the relay K2 indicate it and on the display it is possible to check the kind of alarm. For further information read the manual of the device
• TC: Tribo Probe
• MB-TC: Connection terminal on Tribo probe
• MB: Terminal clamp connection Sequencer
• CS: Connection cable (Screened cable recommended)
|D16||RS485 serial line connection||With this option it is possible to connect the device to a PC by a serial line RS485 to check the running of the device and to set all its parameters by using the software ESAnet made by ESA Electronic Engineering Srl or by Profibus by using external converter.
• The line features are: • 9600 bit/sec • No parity bit • 1 stop bit • No flux control
|GSM1||GSM network connection for SMS sending in case of alarm||GSM network connection by Quad-Band modem 850/900/1800/1900 MHz. When an alarm switch On, the device send an SMS to the mobile phone number insert in set up with the indication of active alarm type (min. and max. dP alarms, dust emission alarms, electrovalves actiovation alarms). By sending an SMS to the SIM mobile phone number of the device iy is possible switch Off all the alarms and receive back a data string with some operating information: Alarms reset command: SMS text = !a Operating information datas sending command: SMS text = !i|
|GSM2||GSM network connection for datas sending to database ESAWEB||GSM network connection by Quad-Band modem 850/900/1800/1900 MHz. The equipment sends some operating data to a database at regular time intervals By accessing the web page via PC, tablet or smartphone it is possible to view and download the stored data. In the event of alarms, data is written to the database even if outside the established time interval.|
|D01||Enable 4 - 20 mA signal|
|D02||Zero adjustment of 4 - 20 mA signal reading|
|D03||4 - 20 mA signal amplification adjustment|
|D04||Average reading of 4 - 20 mA signal|
|D05||Two digital inputs|
|D06||Two digital outputs|